If it's only when the compressor is on, then it's when the belt is under extra load.
Could be the belt slipping.
Could the the tensioner pulley bearing
could be the compressor itself.
Is the AC cold out of the vents?
Thursday, June 25th, 2009 AT 8:02 PM